Huawei H12-425_V2.0-ENU HCIP-Data Center Facility Deployment V2.0 Online Training
Huawei H12-425_V2.0-ENU Online Training
The questions for H12-425_V2.0-ENU were last updated at Feb 29,2024.
- Exam Code: H12-425_V2.0-ENU
- Exam Name: HCIP-Data Center Facility Deployment V2.0
- Certification Provider: Huawei
- Latest update: Feb 29,2024
Which of the following descriptions for the configuration of the PDU8000 modular precision power distribution cabinet is correct?
- A . Modular precision power distribution cabinet supports single and dual input
- B . Modular precision power distribution cabinet supports up to 4 output modules
- C . The output module of the modular precision power distribution cabinet only supports 1P air switch
- D . The input modules of the modular precision power distribution cabinet are MCCB and ATS.
If the customer’s load cannot be powered off, what should be paid attention to disconnecting the maintenance bypass switch after the maintenance is completed?
- A . The circuit module is normal and can supply power
- B . The maintenance bypass switch can also be disconnected when the bypass module is abnormal
- C . EPO filling can break the maintenance switch
- D . The battery input is normal